Programmable Logic Controllers (PLC) will scan very quickly. This can be anywhere from 1 to 20 ms, which translates into 1000 to 500 times each second. But what exactly is a scan?
A scan is when the PLC will complete the following:
Look at all of the inputs to the programmable controller. Digital, Analog, Communication
Solve the logic to determine the output status. PLCs generally will solve the logic from left to right, top to bottom. The output of the rung before is available for the next rung.
This is like some of the popular brands of PLCs like Mitsubishi, Allen Bradley, Siemens, Omron, Automation Direct, etc. There are some exceptions like older Modicon models that solve the logic top to bottom, left to right. Always refer to the manufactures manual to ensure the program execution method.
Diagnostics and Communication:
The PLC will do a self-check. It will verify that no errors exist in memory, cards attached, etc. This is critical because the PLC in an industrial application can have devastating effects if something malfunctions and the machine continues to function erratically. The PLC will stop executing, return the outputs to a normal state, and indicate an error has occurred.
Communication will happen to the remote I/O, operator panels, etc.
Outputs are set according to the PLC program. (Digital, Analog) This is where the physical items will start moving. (Motors, Valves, etc.)
To understand the scan lets take a look at an example.
The following program will look at input X0 and set an internal bit for one scan one on the rising edge of the input and one on the trailing edge of the input. The rising edge is when the input transitions from off to on and the trailing edge is when the input transitions from on to off.
The bits will only be on for one scan so we will increment an internal word by one when the bits go on. This way we will be able to see the bit increment in the word.
Leading-edge one shot (one scan) bit. When the input signal goes on (X0) and C1 is not on, then C0 is turned on. The next rung will have C0 and X0 on so C1 turns on.
Remember: The PLC will scan from left to right, top to bottom and the outputs from the previous rung are available for the next.
C0 is on so the increment will add one to D0.
The next scan X0 is still on, C1 is now on so output C0 is turned off. C0 has been now on for one scan from the transition from off to on.
Trailing edge one shot (one scan) bit. When the input signal goes ooff (X0) and C3 is not on, then C2 is turned on. The next rung will have C2 and not X0 on so C3 turns on.
C2 is on so the increment will add one to D1.
The next scan X0 is still off, C3 is now on so output C2 is turned off. C2 has been now on for one scan from the transition from on to off.
Contact me for the above program. I will be happy to email it to you.
If you have any questions or need further information please contact me.
You can download the software and simulator free at the following address. Also listed are helpful guides to walk you through your first program. Do-more Designer Software
If you’re like most of my readers, you’re committed to learning about technology. Numbering systems used in PLC’s are not difficult to learn and understand. We will walk through the numbering systems used in PLCs. This includes Bits, Decimal, Hexadecimal, ASCII and Floating Point.
To get this free article, subscribe to my free email newsletter.
Use the information to inform other people how numbering systems work. Sign up now.
The ‘Robust Data Logging for Free’ eBook is also available as a free download. The link is included when you subscribe to ACC Automation.