The productivity open P1AM I/O interface chip-set supports the full suite of Productivity 1000 I/O expansion modules. These modules are industry approved and proven in the industrial environment. Modern industrial signal levels for digital and analog inputs and outputs are used.
P1000 modules available to you include the following:
• High-speed Input
We will be adding additional discrete input and output modules (cards) to our P1AM-START1 ProductivityOpen starter kit with Ethernet. A program will then be discussed that will print the modules in our system and then set and reset discrete digital inputs and outputs.
P1-16TR – Productivity1000 relay output module, 16-point, 6-24 VDC/6-120 VAC, (16) Form A (SPST) no-suppression, 2 isolated common(s), 8 point(s) per common, 2A/point, 8A/common.
P1-16CDR – Productivity1000 discrete combo module, Input: 8-point, 24 VAC/VDC, sinking/sourcing, Output: 8-point, 6-24 VDC/6-120 VAC, relay, (8) Form A (SPST) relays, 1A/point.
P1-08SIM – Productivity1000 simulator input module, 8-point.
Let’s get started. Continue Reading!
Math instructions in your Arduino sketches (programs) consist of arithmetic operations, compound operators, absolute, power, square root, sin, cos, tan, random, map and constrain.
These instructions will be generally used with other instructions in your sketch.
We will be looking at each of these instructions that are available using productivity blocks. A sample program will be discussed that will involve some of these math instructions. Let’s get started. Continue Reading!
Data types in the C++ language are used to determine the variable or function applied for the given type. The type will determine the size of the storage (bits), and the method to interpret the information.
Microprocessors can only understand binary (on / off) numbering systems. The interpretation of these binary numbers will allow us to have several different data types. We will be reviewing the different data types that we can use in our sketches (programs) for our P1AM-100 arduino industrial controller. Only the variables data types available in ProductivityBlocks will be discussed, but references will be made for all data types that can be used. We will then look at a program that will list some integer and string variables. This will then be displayed on the serial monitor of the Arduino IDE. Let’s get started. Continue Reading!
The P1AM-100 industrial controller is programmed with the Arduino IDE (Integrated Development Environment). The arduino IDE will allow us to write sketches (programs). These sketches have basic common elements like setup and loop.
We will be looking at these elements in our first program in the Arduino IDE and ProductivityBlocks. We will be modifying our first program with the selector switch. When it is on we will flash the CPU LED light on and off. When it is off we will ensure that the CPU LED light is off. Let’s get started.
Last time we created our first program and transferred this to our connected Productivity 1000 Series PLC. This was programmed with our computer running the Productivity Suite Software. One of the most important aspects of programming the PLC is to document. This will aid you and your team in programming, troubleshooting and modifying the automation control system. Your documentation should read like a book so information can be quickly obtained when required. Time spent on the documentation will be priceless when you go to read your program in 1, 3 or 10 years from now. The Productivity Suite software provides several different methods for documenting your program.
Tag Names and Details, Task Names and Descriptions, Rung Comments and Instruction comments are the ways that we will be looking at documenting our program.
Let’s get started. Continue Reading!
Suppanel is an Android app that is used to create a human machine interface (HMI). This HMI panel can be created on your computer, tablet or phone using the appropriate operating system or software. You can use this software to create panels that you can control or modify values in your automated system. These panels can be shared with other Suppanel users.
We will be creating a Suppanel Panel to monitor and control a Solo Process Temperature Controller via the Click programmable logic controller (PLC). The Click will be communicating to the Solo with serial RS485 using Modbus RTU protocol. The Suppanel HMI will be communicating to the Click PLC using Ethernet Modbus TCP protocol.
Watch on YouTube : Suppanel Android HMI to Click PLC
Let’s get started. Continue Reading!
Data logging does not have to be complicated anymore. The BRX Series PLC can log your specific data up to 32 Gigabits on a Micro SD Card. It will store your data for future data analysis in a CSV (Comma Separated Value) Txt file based on time and/or event.
This is all accomplished with just one instruction in the BRX PLC. Excel is just one program that you can import and analysis this CSV Text file.
Do-More Designer has a Browse PLC File Systems window that will allow you to copy, create and delete the files from the connected computer. This will save you from going to each controller, removing and copying the files on the Micro SD Card.
We will be looking at the data logging instruction in the BRX Series PLC and how to retrieve and view this information. Let’s get started. Continue Reading!
We would like to take a few minutes and reflect on the past, current and future of ACC Automation. 2017 has been our best year yet thanks to you. Your questions, comments and suggestions have helped us to build the site that you see today.
Thank you. Continue Reading!
Serial communication instructions will allow you to send and receive serial data to an external device. The communication method that you setup can be ASCII or numeric (binary). ASCII (American Standard Communication for Information Interchange) can be used to send to devices such as a printer or display.
Receiving ASCII can be used for connecting barcode scanners to the PLC. The barcode will be read as an ASCII string in the PLC.
The BRX Series PLC will allow you to use instructions such as STREAMIN and STREAMOUT to send and receive data from devices mentioned above. They are usually a one to one device and do not have a protocol.
A protocol is like a language used to communicate to different devices connected together. Modbus serial communication (Modbus RTU) is a standard protocol used in many industrial automation devices. The BRX Series PLC has a MRX (Modbus Network Read) and MWX (Modbus Network Write) instructions.
We will demonstrate these instructions by communicating Modbus RTU to a Solo Temperature Controller. (RS485) Our example will read the current process (PV) value and write the set point value (SV) in the controller. Let’s get started. Continue Reading!
Drum instructions are great tools when you have a simple sequence of events that need to occur at a set time interval or as a result of an event. They mimic an electromagnetically drum sequencer. The BRX Series PLC has a drum in the instruction set.
Have you ever seen the mechanisms of a music box? Ok so it’s a little drum with pegs that catch and flick the chimes in a particular sequence to play whatever tune is on the drum. So in the PLC you can have a drum driven by an event, (input from a limit switch or button), or by time.
We will discuss the drum instruction and look at an example of controlling traffic lights with a cross walk signal. Continue Reading!