# How PLC Inputs Work

This post is a further follow up from my original ‘Here’s a Quick Way to Understand PLC Inputs and Outputs’. There are basically two different kinds of PLC inputs, Discrete and analog. Discrete inputs are either ‘ON’ or ‘OFF’; 1 or 0. You can think of them as a single switch. Analog inputs have a range to them. They are inputs that usually will sense pressure, temperature, height, weight, etc.  They usually have one of the following signals that are inputted into the PLC: 4-20mA, 0-10VDC, 1-5VDC.

Discrete Inputs

The above diagram has two inputs. A normally open (NO)  and a normally closed (NC). When we talk about normally open and close, think of the condition of the input if no one touches anything. A normally open contact will not turn on the input to the PLC card in its ‘normal’ state. The normally closed contact will turn on the input to the PLC card in its ‘normal’ state.

Normally Open Input
The NO contact when activated will complete a circuit and turn on the PLC input. Ladder logic will then turn on if you use a normally open (Examine On) input in your program. See above diagram.

Normally Closed Input
The NC contact when activated will break a circuit and turn off the PLC input. Ladder logic will then turn off if you use a normally open (Examine On) input in your program. See above diagram.

As you can see with the diagram above this can get tricky to determine the on/off condition of the input. PLC logic can convert any signal by using normally closed (Examine Off) inputs in the program. In the field, I usually look at the PLC input lights, and wiring diagrams to determine the current state of the input. This is before diving into the program to troubleshoot.

Here is a link to wiring up discrete 3-wire sensors in the field. Here’s a Quick Way to Wire NPN and PNP devices

An analog input converts a voltage or current level into a digital value that can be stored and processed in the PLC. They use words to determine the signal coming from the device.
Example:
4 – 20 mA current Input – 8 bit resolution
4 mA = 00000000 base 2 = 00 base 16
20 mA = 11111111 base 2 = FF base 16
What Everybody Ought to Know About PLC (Programmable Logic Controller) Numbering Systems

In the industrial environment noise from variable frequency drives, improper grounding, etc. can interfere with your analog input. The following post will show a quick method to reduce this noise.
The Secret Of Getting Rid Of Noise On Your Analog Signal

How to make a Start / Stop / Jog circuit in a PLC
The Secret of Using Timers
The Secret of Using Counters

Watch on YouTube : How PLC Inputs Work

Watch on YouTube : Wiring (Testing) Analog PLC Input Click

Watch on YouTube : Wiring (Testing) Analog PLC Input Omron CP1H

Watch on YouTube : Wiring Contact (Discrete) PLC Inputs

Watch on YouTube : Wiring PNP Sensor to PLC

Watch on YouTube : Wiring NPN Sensor to PLC

Thank you,
Garry

If you’re like most of my readers, you’re committed to learning about technology. Numbering systems used in PLC’s are not difficult to learn and understand. We will walk through the numbering systems used in PLCs. This includes Bits, Decimal, Hexadecimal, ASCII and Floating Point.

To get this free article, subscribe to my free email newsletter.

Use the information to inform other people how numbering systems work. Sign up now.