A dusk to dawn sensor usually is discrete on/off of the lighting control. If we want to vary the lights to mimic more of the sunset and rise, we would use an analog output to control the lights. I was recently asked about such a program. Every day they wanted the lights to go off at 10 pm and come back on at 6 am. At 9:30 pm the lights would be on at 70% or 7volts of a 0-10V signal. In the next half hour, the program will bring the lights from 70% down to 0%. In the morning the lights will come back on within the half-hour from 0% to 70%. Poultry Farms are one place that would utilize this program.
We will be developing a program that will do this with our Click PLC. Let’s get started! Keep on Reading!
Stack lights are usually modular stackable components that provide a visually illuminated and audible indication for machines, systems, and processes. They are usually located on top of equipment to provide this notification to personnel in the area.
Stack lights are also known as signal tower lights, indicator lights, warning lights, industrial signal lights, tower lights, and light towers.
We will be connecting a Patlite NPS-402-RYGB Super Slim stack light to our Click PLC.
These stack lights come in preassembled units in the most popular combinations of colours with ABS resin main bodies that offer superior impact and heat resistance; double-insulated construction enhances durability and safety. Interchangeable light modules require no rewiring. Let’s get started. Continue Reading!
The Ethernet Click PLC high speed counter has seven different modes of operation. In Part 1 we discussed the High Speed Count Mode, Interval Measurement Mode,
Duration Measurement Mode and Frequency Measurement Mode.
This 100 KHz counter can accept Up, Down, Up/Down, Pulse/Direction or Quadrature (with Z) inputs.
We will be looking at the last three different high speed counter modes available in the click. (External Interrupt, Pulse Catch, Filter) This is all setup through a user friendly graphical user interface. We will also combine the Frequency Measurement and the High Speed Count in one application. Let’s get started! Keep on Reading!
The Click PLC family has been updated, and now has the ability to use high speed counting. This is available on all of the Ethernet units that have DC inputs. The faster processor on the Ethernet unit (3 to 10 times faster than the basic unit) allows this capability. There are seven (7) different modes of operation for the high speed counter available so adaption to your automation solution is easy. The input can count Up, Down, Up/Down, Pulse/Direction or Quadrature (with Z). Maximum speed on the high speed counter inputs are 100 kHz. That is 100,000 pulses per second.
We will be looking at the different high speed counter modes available in the click. This is all setup through a user friendly graphical user interface. Let’s get started! Keep on Reading!
Firmware is usually PLC operating system code that is written into a read only memory. The BIOS (Basic Input Output System) of a PC (personal computer) is a good example of firmware. It provides the low level interface between the hardware and software. The Click PLC firmware comes with the programming software.
We will be updating our firmware of our Click PLC from 2.10 to 2.30. Let’s get started! Keep on Reading!
The Productivity 1000 series of programmable logic controllers has a slim stackable super compact design. This is sometimes also referred to as a shoebox PLC because of the shape and way in which expansion modules are added. This new Productivity 1000 series PLC is the latest in the Productivity series of controllers that have hit the market.
Productivity 1000 (Stackable Micro PLC)
Productivity 2000 (Micro Modular Programmable Controller)
Productivity 3000 (Modular Programmable Controller)
These three series currently make up the Productivity Series form Automation Direct.
The Productivity 1000 series PLC provides the following features for your automation control panel.
– 50MB user memory – Can handle very complex applications easily.
– 4 built-in communication ports – Easy connectivity to your network. This would include your PC, HMI, Networks, etc.
– Data logging up to 32 GB on a microSD card
– Add up to 15 IO modules to communicate to your field sensors.
– Free Software and 30 days of free training with every CPU from Automation Direct.
– Interactive PLC Configuration Tool
– Tag Names
– Auto-discovery IO – Physical I/O tags will be generated based on each module’s position in the base. You can also reconfigure the setup and assign new tags manually.
– I/O Modules have QR codes under the wiring cover. This can be scanned so you can have the latest specifications/wiring diagrams for the module.
– Limitless PID – Autotuning – Individual or Cascade Mode – etc
– Web Server and Mobile Access
– Advanced Software instruction set
We will be looking at a lot of these features of this powerful controller. Let’s start by looking at the hardware. Continue Reading!
Recently I was asked to demonstrate communication between a Click PLC and BRX PLC using Modbus RTU. Both PLCs are available from automation direct com. Modbus serial communication (Modbus RTU) is a standard protocol used in many automation devices. It works on a Master / Slave configuration. You can have only one master per network on Modbus RTU (Remote Terminal Unit). A maximum of 32 devices (Nodes) on the network can communicate to the master. A review of the Modbus RTU protocol (RTU frames) can be seen at the following URL.
Using the Click PLC as a Master we will be communicating to the BRX PLC (Slave). Our example will read 10 registers from the BRX PLC and write 10 registers to the Click PLC. Let’s get started! Keep on Reading!
The data control instructions in the Omron CP1H programmable logic controller are used to manipulate the outputs based upon control conditions. Control is the main purpose of these instructions within the PLC. Instructions include PID (Proportional, Integral and Derivative), PID with Auto tuning, Dead Band Control, Limit, Dead Zone Control, Time Proportional Output, Scaling, etc.
We will be looking at some of these instructions in the Omron CP1H PLC. Examples of the instructions will be presented. Continue Reading!
The Omron CP1H programmable logic controller has several different table data processing instructions. These instructions are used to handle table data, stacks and other ranges of data.
We can define a stack of data. With this data we can then do the following: add new data by pushing onto the stack, use FIFO (First In First Out), use LIFO (Last In First Out), find the current stack size and read, overwrite, insert or delete from the stack.
Dimension record tables are used to define the length of each record and the number of records. We can then write and read these records. This is ideal for data acquisition projects.
Other instructions found in the table data processing instructions include searching, summing and finding minimum and maximum values.
We will be looking at these instructions in the Omron CP1H PLC. Examples of the instructions will be presented. Continue Reading!