Utilizing the CX Server DDE Manager will allow us to provide a link to the information in the Omron PLC. This link can be placed on an Excel spreadsheet. Charts, graphs, etc., can be made from the data. We will create links on an excel spreadsheet from a CQM1H and a CP1L PLC. The information will then be displayed as a bar graph comparing the first ten memory areas.
What is DDE?
Dynamic Data Exchange (DDE) is a channel through which correctly prepared programs can actively exchange data and control other applications within Microsoft Windows. The DDE manager will allow us to set up all of the links.
Starting the DDE Manager
Under Change PLC, we can now enter the information about how we communicate with the programmable logic controller.
Device Name: – Name in which the DDE Manager will call the PLC
Device Type: – The model of PLC that will be connected
Network Type: – This is the communication method we will use with the device.
In our example, we will use the following two Omron PLCs.
- CQM1H – SYSMAC WAY (Omron Host Link Protocol) Communication Port 11, 9600, E, 7, 2. Unit #00
- CP1L – USB
On the physical tab, we set the following information:
PLC: – This is the list of PLCs entered in the previous step
Data Location: – The memory location that we want to read from
Internal Data Type: – This is the interpretation of the data we read. (Example: Bit, Word, BCD, etc.)
Command Modifier: – This is used if we need to Force Set / Reset the data location. This can be used to override the PLC program. Use with caution.
Press OK when finished setting the address.
Our point is now programmed. You will notice the symbols before the name of the point. This tells us at a glance what type of data we are looking at. Please refer to the CX Server Runtime manual for all symbol meanings.
Start Microsoft Excel
Copy DDE Links to Excel
Go back to the DDE manager and the points under the Project Editor. We can now select the first ten items on the list. Click the first one and then move to the last item. Hold the shift while clicking the last item will select all of them.
Hit the DDE Link icon.
The information will now be displayed and updated on your worksheet.
The update time will depend on the interval set in the DDE Manager. Right-click on the minimized DDE Manager icon and select Update Interval…
We can also set individual point update times in the DDE link item. The default update time is established via the DDE Manager, but we can also set the time in the individual points on the spreadsheet.
DDE Update Default Link:
=CDMDDE|’C:\ACC DDE.cdm’!’\CP1L D0′
5 Second Update Link:
=CDMDDE|’C:\ACC DDE.cdm’!’\CP1L D0,5′
In the Project Editor of the DDE Manager, you can see the first ten memory areas are being used. This is the yellow triangle with the lightning bolt symbol. (You cannot delete the point if it is in use.)
Here is an example of the finished excel file. We have ten memory locations from each PLC listed. We have inserted a graph that will dynamically change when the values are read.
Download the excel file here.
As you can see, implementing the CX Server DDE Manager is not a difficult task. It provides a quick and efficient way to view the needed information.
Excel – Conditional Movement of Data
Watch on YouTube: Implementing the Omron CX Server DDE and Excel
If you have any questions or need further information, please get in touch with me.
If you’re like most of my readers, you’re committed to learning about technology. Numbering systems used in PLCs are not challenging to learn and understand. We will walk through the numbering systems used in PLCs. This includes Bits, Decimals, Hexadecimal, ASCII, and Floating Points.
To get this free article, subscribe to my free email newsletter.
Use the information to inform other people how numbering systems work. Sign up now.
The ‘Robust Data Logging for Free’ eBook is also available as a free download. The link is included when you subscribe to ACC Automation.