The cmore EA9 HMI can connect to the Solo process temperature controller using the built-in RS485 serial communication port. This will connect up to 32 solo units back to the HMI for display and control.
We will be setting up our headless RHMI c-more EA9 to communicate to the Solo process temperature controller. Using the information that we have discussed previously, we will set up data logging, file transfer protocol (FTP), bitmaps, etc.
We will also set up an object library of the Solo 4896 process temperature controller. This will consist of a bitmap, numeric display, numeric edit, indication lights, and up and down increment. The system will then be controlled using the remote applications discussed last time. Let’s get started.
The C-More EA9 HMI Panel through the Ethernet port can send secure email messages. These mail messages with attachments can be sent through a specified mail server.
We will be sending an email using a Gmail account with authentication. This will also include an attached logged data file. We will also discuss how the C-More HMI can send a text (SMS) message. Let’s get started.
The C-More EA9 HMI Panel through the Ethernet port can be set up to use FTP (File Transfer Protocol). FTP is a standard network protocol used to transfer computer files between a client and a server on a computer network.
The C-More HMI can be used as an FTP Client or Server depending on your application.
An FTP client can send and receive files from an FTP server site. You will need an FTP Server already set up in your network to use this feature. (Example: FTP Web Server) See the help file in the C-More software for more information on the Cmore FTP Client Setup and use.
The Cmore FTP Server can retrieve data from the C-more memory with requests from the client. The power of this setup is the ability to automate the retrieval of the information using a batch (BAT) file. We will be setting up the FTP Server function and access the data log that we set up previously using a PC as the client. Let’s get started.
The C-More HMI Panel can log data using the Line Trend Graph or PID Faceplate Trend Graph objects. When Save Log Data is selected on the Options tab configuration for that object, data is written to a “.txt ” file saved to the storage device selected.
Data Logging is commonly used to monitor systems and/or processes taking place at an industrial facility, providing time, date, and current conditions as configured on the Object. Data Logging can be used to collect temperatures, flows, alarms, levels, pressure and just about any instrument measurable condition.
We will be data logging from a Line Trend Graph. A register (word) made up of bits will also be logged. We will log this information every second on our USB stick. Starting/stopping the logging can be controlled on the HMI as well as USB reject. Once the USB is ejected, it can then be connected to our computer to review the files. We will also view and download the files from our web server that we enabled last time on our C-More EA9 HMI panel. Let’s get started.
The C-More HMI Panel can function as a simple web server. A web server includes software and hardware that will respond to World Wide Web client requests. The communication used between client and server takes place using the Hypertext Transfer Protocol. (HTTP). Information generally takes the form of pages that may include images, style sheets and scripts in addition to the page text contents. Remote access will allow for viewing or controlling the C-More EA9 HMI. We can use any windows based machine or use the C-More remote HMI App from Apple iTunes store, Google Play or Amazon App Store for mobile devices.
We will turn on the web server functionality in our HMI panel. Using a web browser (Chrome), we will connect to our C-More EA9 HMI. We will then download the remote access software from the website. We will then run this remote access software to control our existing HMI program. Let’s get started.
The C-More HMI Panel software uses virtual components called Objects. These objects are programmable to simulate the functions that you require on your automation project. Pushbuttons, Switches, meters, and graphs are just a few of the objects that are available to you.
The Text List Objects include a variety of options to customize the display of text on a screen.
We will now look at the object list text that we can use with our HMI panel. The text objects that are available on the C-More EA9 are Static, Triggered, Lookup, Dynamic, Bitmap and Text Entry. We will program each of these text objects. Let’s get started.