All Solo Standard Process Temperature Controllers that support RS-485 serial communications can use the SL-SOFT configuration and monitoring software. This free package will communicate to monitor multiple SOLO controllers using Modbus RTU or Modbus ASCII protocols.
We will be installing the SL-SOFT configuration and monitoring software package on our Windows 10 PC. Communicating through our Waveshare USB to RS485 adapter, Modbus RTU will be used as the protocol to establish communication. Let’s get started. Keep on Reading!
We will be installing an industrial USB to RS485 converter on our computer. The Waveshare USB to serial port is a 2-wire USB to RS-485 serial communication adapter for RS485 use. It does not require an external power supply or complicated configuration.
It has a Type A (plug) USB connector for the computer side and screw terminals for the RS485 connections. This is an industrial USB to RS485 converter that has an FT232RL chip inside. It features embedded protection circuits such as lightning-proof, resettable fuse, ESD (Electrostatic Discharge) protection, and TVS (Transient Voltage Suppression) diode, etc. All of these features are packed within a small form size. Purchase at Amazon.com
We will be installing the driver for this USB to serial converter and connecting it to our computer. Node-RED will be used to communicate Modbus RS485 protocol to a Solo process temperature controller. Let’s get started. Continue Reading!
The cmore EA9 HMI can connect to the Solo process temperature controller using the built-in RS485 serial communication port. This will connect up to 32 solo units back to the HMI for display and control.
We will be setting up our headless RHMI c-more EA9 to communicate to the Solo process temperature controller. Using the information that we have discussed previously, we will set up data logging, file transfer protocol (FTP), bitmaps, etc.
We will also set up an object library of the Solo 4896 process temperature controller. This will consist of a bitmap, numeric display, numeric edit, indication lights, and up and down increment. The system will then be controlled using the remote applications discussed last time. Let’s get started. Continue Reading!
The SOLO Temperature Controller is a single loop dual output process temperature controller that can control both heating and cooling simultaneously. It is available in 1/32, 1/16, 1/8, and 1/4 DIN panel sizes and is UL, CUL and CE approved. The name of the temperature controller is deceiving. This unit will also accept voltage and current into them, which is great for process control.
Recently I was asked: How you can change the pressure value from PSI to Bar?
They were bringing into the controller a voltage signal. This can be scaled using the tP-H (High-level signal) and tP-L (Low-level signal). The units on the display scaled for you. The default is -999 to 999. See section 11-2 of the following information guide that comes with the controller. Continue Reading!
We would like to take a few minutes and reflect on the past, current and future of ACC Automation. You have help us succeed in our best year yet.
Starting off we learned how to: Create a PLC with HMI Training and Learning Environment Free – Utilized the Do-More Designer Software and the AdvancedHMI Software we communicated Modbus TCP to the Do-More simulator. This was all done on one computer without any need for additional hardware. The best thing about this was that the investment was only time learning the packages.Continue Reading!
The SOLO Temperature Controller is a single loop dual-output process temperature controller that can control both heating and cooling simultaneously. It is available in 1/32, 1/16, 1/8 and 1/4 DIN panel sizes and is UL, CUL and CE approved.
There are four types of control modes:
PID (Auto Tuning (AT) function) – Solo Control Modes
P stands for proportional and accounts for present values of the error – It reacts to the amount of error which is the difference between the SP (Set Point) and the PV (Present Value) I stands for integral and accounts for past values of the error – It uses math to basically find the approximation of the area under the curve. D stands for derivative and accounts for possible future values of the error, based upon the rate of change – It uses math to determine the slope of the error over time and multiply this by the derivative gain. AT – Auto-Tuning as the name implies will automatically cycle your control system through two cycles and set the PID parameters.
ON / OFF – Solo Control Modes
On/Off control is the simplest form of control. In the case of temperature, the output will be on when the temperature is below-set point. When the temperature gets above the set point of the controller the output will be off. When this cycling occurs frequently, you can add hysteresis to the output. This will limit the time the output goes on and off by a number of degrees.
Manual – Solo Control Modes
Manual mode is when you need to control the output directly. By entering manual mode the operator can adjust the values of the output(s).
Ramp / Soak control – Solo Control Modes
The Ramp / Soak control mode is used to control the outputs according to the pre-programmed SP patterns with the PID control method. The Solo can have eight programs with eight steps each. Note: This can be increased with the additional use of hardware and software via HMI or PLC.
Output Types – Solo Process Temperature Controller
The available outputs include relay, voltage pulse, current, and linear voltage. There are up to three alarm outputs available to allow seventeen alarm types in the initial setting mode. SOLO can accept various types of thermocouple, RTD, or analog input. This means that cascade control is possible with these controllers.
When you use the output of one of the Solo process controllers as the input to another, this would be cascade control.
Modbus RTU and Modbus ASCII Communication
It has a built-in RS-485 interface using Modbus slave (ASCII or RTU) communication protocol.
The Solo Process Temperature Controller can be configured through the buttons on the front of the unit or by the configuration software. Monitoring of up to four controllers at once can be done through the same configuration software.
The following is the wiring of the Modbus Serial communication. We will use a USB to RS485 converter from Automation Direct. (USB-485M)
Installation and operation instructions can be found at the following link: USB to RS485 PC Adapter Installation
The solo process temperature controller needs to be set up before we can communicate to it. The default setting is ‘Off’ for the On-Line Configuration. Here is the way to change into the different modes in the Solo.
In the Initial Setting Mode we will change the online configuration and make the changes to the Modbus settings as follows: 9600 Baud, Even, 7 Data Bits, 1 Stop Bit, Modbus ASCII Format. We will leave the default unit number as 1.
The configuration and monitoring software does not have to be installed. You just need to download the file “slsoft.zip”.
Once downloaded right click on the file and select “Extract All…”. The file ADC1105.exe can now be run.
The recommended screen resolution is 1024 x 768. If you do not have this resolution then there is another program that will allow us to create a shortcut to this program and change our default resolution. After we exit the program, our screen resolution will return to its original state.
Download the exe file (reso.exe) into the same extracted folder that you have the ADC1105.exe file.
Click on the reso.exe file in the folder to run the application.
Click the Browse… button and select the ADC1105.exe solo configuration software.
Under the Graphics Mode: Resolution: select 1024×768 We can leave the rest to the defaults as shown below. Now Click Create Shortcut. Put the shortcut in the same directory as the software that was downloaded.
We will receive notification that the shortcut was created. Click OK.
Our folder will now look like this.
Click on our shortcut (ADC1105 (at 1024×768)) to start the Automation Direct Solo Series Configuration Software.
There are six icons on the main menu. Follow these in order from left to right to set up or troubleshoot your system.
Under the Com port setup, we configure the serial port of the computer to communicate to the Solo. In our case we will use COM5, 9600, Even, 7 Data Bits, 1 Stop Bit, Modbus ASCII Format.
In the Configuration menu, we will select the address of the controller that we will be communicating. This will be the default of the Solo which is 1.
Selecting Connect will then communicate to the Solo process temperature controller and you will see on the screen a picture of the controller with the PV, SV and indicator lights active.
This screen will now allow you to set up all of the parameters in the Solo. Once you enter a value it will be red on the screen. After hitting enter on the keyboard and the value will then be sent to the controller and be displayed in black again.
The recorder screen is used to monitor the temperature over time. You can monitor up to ten Solo Controllers at once.
Command Test is used to send individual Modbus command out. This is done in Hexadecimal.
The software for the Solo Process Temperature Controllers is very functional. Using the Reso software, you will be able to put the Solo Software in the 1024 x 768 that it was created for without manually changing the screen every time.
If you’re like most of my readers, you’re committed to learning about technology. Numbering systems used in PLC’s are not difficult to learn and understand. We will walk through the numbering systems used in PLCs. This includes Bits, Decimal, Hexadecimal, ASCII and Floating Point.
To get this free article, subscribe to my free email newsletter.
Use the information to inform other people how numbering systems work. Sign up now.
The ‘Robust Data Logging for Free’ eBook is also available as a free download. The link is included when you subscribe to ACC Automation.