The cmore EA9 HMI has an event manager that can be used to trigger actions based on various events.
We will be adding a Click PLC to our headless RHMI cmore EA9 program that we created last time to communicate to the solo process temperature controller. The Solo will be connected via RS485 using the Modbus RTU protocol. Using the Modbus TCP protocol we will connect the Click PLC to the Ethernet port. Using the event manager we will be writing the set value (SV) and present value (PV) of the solo process temperature controller to the Click PLC. We will also allow the Click PLC to write the SV into the solo. This is in addition to the writing of the set value via remote apps and the solo itself. Let’s get started. Continue Reading!
The cmore EA9 HMI can connect to the Solo process temperature controller using the built-in RS485 serial communication port. This will connect up to 32 solo units back to the HMI for display and control.
We will be setting up our headless RHMI cmore EA9 to communicate to the Solo process temperature controller. Using the information that we have discussed previously, we will set up data logging, file transfer protocol (FTP), bitmaps, etc.
We will also set up an object library of the Solo 4896. This will consist of a bitmap, numeric display, numeric edit, indication lights and up and down increment. The system will then be controlled using the remote applications discussed last time. Let’s get started. Continue Reading!
The C-more headless EA9-RHMI is programmed using the C-more Programming Software, EA9-PGMSW. The developed project is transferred from the PC to the HMI by either a USB or an Ethernet connection between the two. Previously we used the Ethernet connection to establish communication.
We will be using the USB connection to establish communication, save the program and review the setup screens of the Headless C-more.
Troubleshooting of the USB connection and windows driver will also be discussed. Let’s get started. Continue Reading!
The C-More EA9 HMI Panel now comes in a headless version. (EA9-RHMI) All of the great features that are already built into the EA9 are available with the new headless model. This unit can be mounted within the cabinet and you can decide how to display the information.
This user-friendly, time-saving software platform allows your system data to now be shown to the operators in new ways thanks to the C-More headless HMI panel. Capabilities like data logging, FTP (File Transfer Protocol), secure email, remote HMI and data sharing can now be added to existing PLC hardware.
We will be unboxing this EA9-RHMI unit. Once power is supplied to the unit we will then establish communication and save the program. Let’s get started. Continue Reading!
The C-More EA9 HMI Panel through the Ethernet port can send secure email messages. These mail messages with attachments can be sent through a specified mail server.
We will be sending an email using a Gmail account with authentication. This will also include an attached logged data file. We will also discuss how the C-More HMI can send a text (SMS) message. Let’s get started. Continue Reading!
The C-More EA9 HMI Panel through the Ethernet port can be set up to use FTP (File Transfer Protocol). FTP is a standard network protocol used to transfer computer files between a client and a server on a computer network.
The C-More HMI can be used as an FTP Client or Server depending on your application.
An FTP client can send and receive files from an FTP server site. You will need an FTP Server already set up in your network to use this feature. (Example: FTP Web Server) See the help file in the C-More software for more information on the Cmore FTP Client Setup and use.
The Cmore FTP Server can retrieve data from the C-more memory with requests from the client. The power of this setup is the ability to automate the retrieval of the information using a batch (BAT) file. We will be setting up the FTP Server function and access the data log that we set up previously using a PC as the client. Let’s get started. Continue Reading!
The C-More HMI Panel can log data using the Line Trend Graph or PID Faceplate Trend Graph objects. When Save Log Data is selected on the Options tab configuration for that object, data is written to a “.txt ” file saved to the storage device selected.
Data Logging is commonly used to monitor systems and/or processes taking place at an industrial facility, providing time, date, and current conditions as configured on the Object. Data Logging can be used to collect temperatures, flows, alarms, levels, pressure and just about any instrument measurable condition.
We will be data logging from a Line Trend Graph. A register (word) made up of bits will also be logged. We will log this information every second on our USB stick. Starting/stopping the logging can be controlled on the HMI as well as USB reject. Once the USB is ejected, it can then be connected to our computer to review the files. We will also view and download the files from our web server that we enabled last time on our C-More EA9 HMI panel. Let’s get started. Continue Reading!
The C-More HMI Panel can function as a simple web server. A web server includes software and hardware that will respond to World Wide Web client requests. The communication used between client and server takes place using the Hypertext Transfer Protocol. (HTTP). Information generally takes the form of pages that may include images, style sheets and scripts in addition to the page text contents. Remote access will allow for viewing or controlling the C-More EA9 HMI. We can use any windows based machine or use the C-More remote HMI App from Apple iTunes store, Google Play or Amazon App Store for mobile devices.
We will turn on the webserver functionality in our HMI panel. Using a web browser (Chrome), we will connect to our C-More EA9 HMI. We will then download the remote access software from the website. We will then run this remote access software to control our existing HMI program. Let’s get started. Continue Reading!
The C-More HMI Panel will support a barcode scanner (barcode reader) input. A scanner uses a light source and a light sensor to translate optical impulses into an electrical signal. The CMore can accept a USB barcode scanner input.
We will now connect and program a barcode scanner into our HMI panel. The PLC ladder logic will then be modified to take action on the barcode input. Let’s get started. Continue Reading!
The C-More HMI Panel software uses virtual components called Objects. These objects are programmable to simulate the functions that you require on your automation project. Pushbuttons, Switches, meters, and graphs are just a few of the objects that are available to you.
The Clock Objects includes a couple of options to customize the display of a real-time clock (RTC) on a screen.
We will now look at the object list clock that we can use with our HMI panel. The clock objects that are available on the C-More EA9 are analog and digital. We will program each of these text objects. The source for the RTC clock will also be discussed and programmed both externally and internally. Let’s get started. Continue Reading!