The Stride Field Remote I/O Modules are simple and compact. They provide an economical means to connect inputs and outputs to an Ethernet Modbus TCP communication network. Every module operates as a standalone Modbus TCP server and can be configured via a built-in web server.
We will be looking at the following two Stride Remote IO Modules:
SIO-MB12CDR – Ethernet Modbus TCP Remote IO
– STRIDE discrete combo remote module, Input: 8-point, 12-24 VDC, sinking, Output: 4-point, relay, (4) Form C (SPDT) relays, 2A/point, (1) Ethernet (RJ45) port(s), Modbus TCP server.
SIO-MB04ADS – Ethernet Modbus TCP Remote IO
– STRIDE analog remote input module, 4-channel, current/voltage, 16-bit, isolated, input current signal range(s) of +/- 20 mA, input voltage signal range(s) of +/- 10 VDC, (1) Ethernet (RJ45) port(s), Modbus TCP server, external 20-30 VDC required.
We will be unboxing both of these units. Powering and then setting them up (configuring) via the webserver. Let’s get started. Continue Reading!
The cmore EA9 HMI has an event manager that can be used to trigger actions based on various events.
We will be adding a Click PLC to our headless RHMI cmore EA9 program that we created last time to communicate to the solo process temperature controller. The Solo will be connected via RS485 using the Modbus RTU protocol. Using the Modbus TCP protocol we will connect the Click PLC to the Ethernet port. Using the event manager we will be writing the set value (SV) and present value (PV) of the solo process temperature controller to the Click PLC. We will also allow the Click PLC to write the SV into the solo. This is in addition to the writing of the set value via remote apps and the solo itself. Let’s get started. Continue Reading!
Accelerate Learning …
It is a good time to be in the automation business. Technologies are merging and communicating like never before. What was impossible is now possible for the industrial plant floor. We are looking forward to the New Year and new possibilities for implementing your control solution.
Each year we like to take a few minutes and reflect on the past, current, and future of ACC Automation. You have helped us to build the site that you see today through questions, comments, and suggestions. Thank you.
2019 has been our best year yet thanks to you. Keep on Reading!
We will now wire a stack light to the Click PLC. Stack lights are usually modular stackable components that provide a visually illuminated and audible indication for machines, systems, and processes. They are usually located on top of equipment to provide this notification to personnel in the area.
Stack lights are also known as signal tower lights, indicator lights, warning lights, industrial signal lights, tower lights, and light towers.
We will be connecting a Patlite NPS-402-RYGB Super Slim stack light to our Click PLC.
These stack lights come in preassembled units in the most popular combinations of colours with ABS resin main bodies that offer superior impact and heat resistance; double-insulated construction enhances durability and safety. Interchangeable light modules require no rewiring. Let’s get started. Continue Reading!
Suppanel is an Android app that is used to create a human machine interface (HMI). This HMI panel can be created on your computer, tablet or phone using the appropriate operating system or software. You can use this software to create panels that you can control or modify values in your automated system. These panels can be shared with other Suppanel users.
We will be creating a Suppanel Panel to monitor and control a Solo Process Temperature Controller via the Click programmable logic controller (PLC). The Click will be communicating to the Solo with serial RS485 using Modbus RTU protocol. The Suppanel HMI will be communicating to the Click PLC using Ethernet Modbus TCP protocol.
Watch on YouTube : Suppanel Android HMI to Click PLC
Let’s get started. Continue Reading!