Data logging does not have to be complicated anymore. The BRX Do-More Series PLC can log your specific data up to 32 Gigabits on a Micro SD Card. It will store your data for future data analysis in a CSV (Comma Separated Value) Txt file based on time and/or event.
This is all accomplished with just one instruction in the BRX PLC. Excel is just one program that you can import and analyze this CSV Text file.
Do-More Designer has a Browse PLC File Systems window that will allow you to copy, create and delete the files from the connected computer. This will save you from going to each controller, removing and copying the files on the Micro SD Card.
We will be looking at the data logging instruction in the BRX Series PLC and how to retrieve and view this information. Let’s get started. Continue Reading!
We will now look at the drum instruction in our BRX Do-More Controller. Drum instructions are great tools when you have a simple sequence of events that need to occur at a set time interval or as a result of an event. They mimic an electromagnetic drum sequencer. The BRX Series PLC has a drum in the instruction set.
Have you ever seen the mechanisms of a music box? Ok, so it’s a little drum with pegs that catch and flick the chimes in a particular sequence to play whatever tune is on the drum. So in the PLC, you can have a drum driven by an event, (input from a limit switch or button), or by time.
We will discuss the drum instruction and look at an example of controlling traffic lights with a cross walk signal. Continue Reading!
Math instructions are used to perform mathematical calculations. The BRX Do-More PLC has math instructions that can be used in a wide variety of applications. We will be looking at the INC increment, DEC decrement, LERP linear Interpolation, RANDSEED Random Number Seed, and the MATH Calculated Expression instructions. The automation system that you implement may involve some or all of these instructions. As a system integrator, you will require the use of these instructions in your commissioned programs.
Let’s get started with the BRX Do-More PLC Math Instructions. Continue Reading!
The BRX Do-More series of programmable logic controllers has built in high speed inputs and outputs. Every CPU will have either 6 or 10 high speed inputs (HSI) available depending on the model. These inputs can be used for input frequencies from 0 to 250Khz. 250Khz represents 250000 input counts per second that can be coming from devices connected to your PLC like an encoder. Every BRX Do-More CPU unit also has 2, 4 or 8 high speed outputs (HSO) available depending on the model. The outputs can send a frequency of pulses out up to 250Khz. Due to the speed of the IO, these functions available on the BRX Do-More PLC will operate asynchronous with the PLC scan time.
We will be looking at sending an output of pulses at different frequencies from our BRX Do-More PLC and inputting these back into the high speed inputs of the PLC. So our output will be wired back into our input. We will then display the frequency of the input pulses and the count. As a system integrator, this ability to send and receive high speed inputs and outputs can prove very useful to you in the field when commissioning your automation system.
Let’s get started with the BRX Do-More PLC High Speed IO. Continue Reading!
A majority of the programmable logic controller (PLC) programs will include a counter instruction. The BRX Do-More series of programmable logic controllers have several different counters available for your program. There are five different basic counter instructions in the PLC. The memory area for counters (CT) includes the Counter PVs (Present Values) Counter SVs (Set Values) and the Counter Completion Flags. The default size of the counter area is CT0 – CT255. This size can change to the amount that we need for our program. Please see BRX Do-More PLC Numbering Systems and Addressing on how to change the memory configuration of the controller.
We will be looking at the counter instructions in the BRX Do-More PLC along with some programming examples. As a system integrator, this ability can prove very useful to you in the field when commissioning your automation system. When dealing with counters, we need to look at timing charts. The Secret of Using Counters is a good refresher on using timing charts.
Let’s get started with the BRX Do-More PLC Counters. Continue Reading!