One of the features of the BRX Series PLC is the ability to expand its capability to fit your application. Software and hardware changes are ongoing so the PLC can grow with your needs. Communication is something that the BRX PLC can do very well. As part of the internet of things (IoT), the BRX will share and exchange data. You can also refer to this as the industrial internet of things. This will suit several industrial applications.
The Do-more Updates Release 2.5.2 on April 22, 2019, has introduced new instructions. Here are the instructions that we will be using: HTTPCMD – HTTP Request / Response with Server (BRX only) JSONPARSE – Parse JSON Text (BRX only)
We will be using these instructions to read the weather conditions from a website. Let’s get started. Continue Reading!
Data logging does not have to be complicated anymore. The BRX Series PLC can log your specific data up to 32 Gigabits on a Micro SD Card. It will store your data for future data analysis in a CSV (Comma Separated Value) Txt file based on time and/or event.
This is all accomplished with just one instruction in the BRX PLC. Excel is just one program that you can import and analysis this CSV Text file.
Do-More Designer has a Browse PLC File Systems window that will allow you to copy, create and delete the files from the connected computer. This will save you from going to each controller, removing and copying the files on the Micro SD Card.
We will be looking at the data logging instruction in the BRX Series PLC and how to retrieve and view this information. Let’s get started. Continue Reading!
Serial communication instructions will allow you to send and receive serial data to an external device. The communication method that you setup can be ASCII or numeric (binary). ASCII (American Standard Communication for Information Interchange) can be used to send to devices such as a printer or display.
Receiving ASCII can be used for connecting barcode scanners to the PLC. The barcode will be read as an ASCII string in the PLC.
The BRX Series PLC will allow you to use instructions such as STREAMIN and STREAMOUT to send and receive data from devices mentioned above. They are usually a one to one device and do not have a protocol.
A protocol is like a language used to communicate to different devices connected together. Modbus serial communication (Modbus RTU) is a standard protocol used in many industrial automation devices. The BRX Series PLC has a MRX (Modbus Network Read) and MWX (Modbus Network Write) instructions.
We will demonstrate these instructions by communicating Modbus RTU to a Solo Temperature Controller. (RS485) Our example will read the current process (PV) value and write the set point value (SV) in the controller. Let’s get started. Continue Reading!
Drum instructions are great tools when you have a simple sequence of events that need to occur at a set time interval or as a result of an event. They mimic an electromagnetically drum sequencer. The BRX Series PLC has a drum in the instruction set.
Have you ever seen the mechanisms of a music box? Ok so it’s a little drum with pegs that catch and flick the chimes in a particular sequence to play whatever tune is on the drum. So in the PLC you can have a drum driven by an event, (input from a limit switch or button), or by time.
We will discuss the drum instruction and look at an example of controlling traffic lights with a cross walk signal. Continue Reading!
PLC shifting instructions will move bits in memory areas a fixed amount when instructed. Bits are on/off, 1 or 0 and are usually associated together to form a memory location. The memory location can be used for numbers or positions. PLC BITS NUMBERS AND POSITION is a post that will review the different methods that the PLC will interpret the information in memory
We will be looking at the shifting (moving) of the bits within the memory location in several different ways. ROTL rotate left, ROTR rotate right, Math shift left operator, Math shift right operator, Math unsigned shift right operator and SR shift register are some of the instructions in our BRX PLC that will shift bits.
Let’s look at some samples of each of the above mentioned instructions. Continue Reading!
The program control instructions will allow us to specify what parts of the logic get solved and when this happens. This will control how the PLC will scan and solve your logic in your program using a synchronous PLC Scan. Understanding the PLC program scan will explain the synchronous and asynchronous program scanning. Ladder logic programs get solved left to right, top to bottom. The result of the rung before is available for the next rung.
Using programs, tasks and subroutines in our BRX Series PLC we can divide up our program into smaller segments. This will help when we troubleshoot the system in the field as the system integrator. Let’s look at some samples of each of the above mentioned methods. Continue Reading!
Math instructions are used to perform mathematical calculations. The BRX PLC has math instructions that can be used in a wide variety of applications. We will be looking at the INC increment, DEC decrement, LERP linear Interpolation, RANDSEED Random Number Seed and the MATH Calculated Expression instructions. Your automation system that you implement may involve some or all of these instructions. As a system integrator you will require the use of these instructions in your commissioned programs.
Let’s get started with the BRX PLC Math Instructions. Continue Reading!
Compare instruction are often used in PLC programs to test pairs of values. The output of this comparison conditions the logical continuity of a rung. The BRX series of programmable logic controllers has the following compare contact instructions.
= (if Equal contact)
<> (if Not Equal contact)
> (if Greater Than contact)
>= (if Greater Than or Equal contact)
< (if Less Than contact)
<= (if Less Than or Equal contact)
Besides these instruction the BRX PLC will also have compare instructions for the built in real time clock of the system. We will be looking at these instructions along with some programming examples. As a system integrator, this ability can prove very useful to you in the field when commissioning your automation system.
Lets get started with the BRX PLC Compare Instructions. Continue Reading!
The BRX series of programmable logic controllers has built in high speed inputs and outputs. Every CPU will have either 6 or 10 high speed inputs (HSI) available depending on the model. These inputs can be used for input frequencies from 0 to 250Khz. 250Khz represents 250000 input counts per second that can be coming from devices connected to your PLC like an encoder. Every BRX CPU unit also has 2, 4 or 8 high speed outputs (HSO) available depending on the model. The outputs can send a frequency of pulses out up to 250Khz. Due to the speed of the IO, these functions available on the BRX PLC will operate asynchronous with the PLC scan time.
We will be looking at sending an output of pulses at different frequencies from our BRX PLC and inputting these back into the high speed inputs of the PLC. So our output will be wired back into our input. We will then display the frequency of the input pulses and the count. As a system integrator, this ability to send and receive high speed inputs and outputs can prove very useful to you in the field when commissioning your automation system.
Let’s get started with the BRX PLC High Speed IO. Continue Reading!
A majority of the programmable logic controller (PLC) programs will include a counter instruction. The BRX series of programmable logic controllers have several different counters available for your program. There are five different basic counter instructions in the PLC. The memory area for counters (CT), include the Counter PVs (Present Values) Counter SVs (Set Values) and the Counter Completion Flags. The default size of the counter area is CT0 – CT255. This size can change to the amount that we need for our program. Please see BRX PLC Numbering Systems and Addressing on how to change the memory configuration of the controller.
We will be looking at the counter instructions in the BRX PLC along with some programming examples. As a system integrator, this ability can prove very useful to you in the field when commissioning your automation system. When dealing with counters, we need to look at timing charts. The Secret of Using Counters is a good refresher on using timing charts.
Let’s get started with the BRX PLC Counters. Continue Reading!